|Type:||Asynchronous Motor||Phase:||Single-phase OR Three-phase|
|Efficiency:||IE 1||Product Name:||Air Cooler Fan Motor|
|Protection Class:||IP21||Winding:||Copper Wire|
150W Air Cooler Fan Motor,
AC220V Air Cooler Fan Motor,
1200r/min universal electric fan motor
Specification for Air Cooler Fan Motor:
We also have other motors used for Range hood , Air Conditioner/ Air Cooler ,ventilator confirm to CCC standard ,with high efficiency ,good proformance,energy saving , lowest noise ,high starting torque,big air flow,dustproof , anticorrosion ,long service time .
Technical Parameters for Air Cooler Fan Motor:
|Speed R. P. M||500-2600r/min|
|Type||Asynchronous Air Cooler Fan Motor|
|Efficiency||IE1, IE2, IE3, IE4|
|Insulation Class||E, B, F|
|Air Cooler Fan Motor||Air Conditioning|
|Use||Fan Motor for Air Conditioner, air cooler, cleaner,Fan Coil Unit and Other HVAC Systems|
|Certification||CCC, CE, RoHS, UL, VDE|
More Items of Air Cooler Fan Motor:
More Features for Air Cooler Fan Motor:
• Reversible plug for easy rotation
• Class B Insulation
• Quick installation
• Energy efficient
• Quiet operation
• Ball bearing
• Diameter: Steel cover 140mm
• Automatic overload
• Operating temp -10-43 degree
• Power:420W or as your request
• Rated Frequency:50/60Hz
• Number of Pole:2/4/6/8/10Pole
• Shaft size:12/12.7/14mm
• Speed: 1200rpm
• Thermal protection
• Usage: air cooler machine
• High efficiency,High reliability,Little vibration,Low noise Specifications
B. long work times and Low temperature
E.large loading capacity
To test the fan motor for air cooler on your air conditioner, you’ll have to do a continuity test. Click here for a video tutorial. Before you start, make sure the thermostat is set to cool and that the temperature setting is as low as it will go.
Step 1. Check the power
If you suspect the fan motor for air cooler is bad, the first thing you should check is the power to the motor and the power to the air conditioning unit. Locate the circuit breaker and ensure it hasn’t tripped. If the power is fine, check to see if there is proper voltage. You can do this at the transformer, checking for a fuse in the low-voltage circuit.
Step 2. Check the windings
Next, check the windings of the fan motor for an open or a short. To do this, you’ll have to measure the ohms. If your fan motor is a 120V, it will most likely have four colored wires (black, blue, red, yellow, etc.), as well as a white wire, a black wire, and two brown wires. If you’re working with the wires, do a resistance check between the white wire and each of the colored wires. The higher the resistance is, the lower the speed is, with each colored wire representing a different speed.
Look for a resistance reading. A reading of zero means the fan motor winding is likely shorted and causing the breaker to trip or blow. An infinite reading, on the other hand, may indicate an open motor winding. If either of these conditions exists, the fan motor needs to be replaced.
Step 3. Inspect the capacitor
Keep in mind that just because the fan motor for air cooler isn’t running, doesn’t mean it’s bad. If the power supply is fine and the windings are in good shape, check the capacitor next.
The capacitor helps the fan motor for air cooler run. Delivering torque to the fan motor for air cooler, if the capacitor is faulty, there won’t be enough power delivered and the blower wheel, fan belt, and other important components can cease to operate.
To inspect the capacitor, make sure it is discharged. Once it is discharged, use a capacitor tester to check the microfarad reading. The reading should be within 10 percent of the rated capacitance on the capacitor. If the reading doesn’t match the rating, replace the capacitor.
This series of motors are specially developed for dehumidifiers. They have the characteristics of low noise, high efficiency and stable operation. Fan motor for air cooler can be used for dehumidification in various places, and can be customized according to customer’s requirements.
AC Fan Motor for Air Cooler Maintenance
The fan motor for air cooleris one of the most important components of your air conditioning system. Often referred to as the “heart” of HVAC equipment, fan motors for air cooler work hard and under tough conditions for years. While fan motors for air cooler don’t need much, overlooking maintenance can have a serious impact on your air conditioning system and the comfort of your home.
Sometimes, replacing the fan motor in your air conditioning system is inevitable, but with routine maintenance, you can prolong the lifespan of your air conditioner. When it comes to fan motor for air cooler burnout, dirt is the biggest culprit. That’s why the best thing you can do is to keep everything clean. When dirt builds up in the fan motor for air cooler, it can block the motor hole and cause the component to overheat.
Contact Person: Nana